Babel Buster BB2-7010 BACnet IP to Modbus Gateway provides a BACnet IP client and server, Modbus TCP client and server, and Modbus RTU port configurable to be client or server. The BB2-7010 BACnet IP client allows BACnet IP devices to be accessible from Modbus TCP or RTU. You configure the device instance, object type and instance, and poll interval for reading or writing BACnet objects. The object data is stored in the BB2-7010 server for subsequent retrieval as Modbus registers. When used to connect Modbus devices to a BACnet IP network, the BB2-7010 is configured via simple web page templates to read and write Modbus registers in one or more Modbus servers, making that data accessible as BACnet objects on the BACnet IP network.
Modbus RTU, Modbus TCP
Read/Write any standard Modbus register via BACnet ; Read/Write any standard BACnet object via Modbus; Up to 1,000 BACnet objects; Bidirectional communication between BACnet and Modbus; Supports Modbus coils, input registers, holding registers; Single or double Modbus registers; Signed, unsigned, IEEE 754 Modbus registers; Supports Mod-10 format (2, 3, 4-register); Modbus register mapping configured via web interface; Modbus registers may be scaled (x10, x0.1, etc.); Modbus (master) polling interval configurable per point; Commandable BACnet objects implement priority array; Hardened EIA-485 transceiver for Modbus RTU; Optional RS-232 transceiver (in place of RS-485); 10/100BaseT Ethernet for BACnet IP and Modbus TCP; Powered by 10-30VDC or 12-24VAC 50/60 Hz; Power Consumption: 0.3A @ 24VDC; DIN rail mounting, 100mm H x 70mm W x 60mm D; Pluggable screw terminal block for power & RTU network; Operating temperature -40?C to +85?C; Humidity 5% to 90%; FCC Class A, CE Mark; Listed to UL 916 and (Canadian) C22.2 No. 205-M1983
See attached spec. sheet.